Last updated on January 30th, 2021 at 05:37 pm

For calculating specific power consumption in compressed air. we need to calculate output of the air compressor. Output of air compressor can be calculated in terms of free air discharge. Let us discuss how to calculate FAD at shop floor

**Methodology :**

Calculating free air discharge at shop floor is very easy, we need to just isolate Air compressor from normal operation and require one air receiver for getting free air discharge (FAD) of air compressor.

Step by step process is explained below:-

**Instrument required**: Pressure gauge (1 Nos), Timer (1
Nos), Volume of vessel and line holdup.

**Step -1**: Prepare compressor for measurement,
Isolate Air receiver and hookup with the compressor you want to measure air
discharge.

**Step -2:** Measure holdup volume(**V**) of air compressor and pipeline .

**Step -3:** Drain moisture if available in recover and
pipeline and then close all drains.

**Step -4:** Note initial pressure (**P _{1}**) at air compressor. it is recommended to keep initial
vessel pressure above atmospheric pressure for at least 5min, this will ensure
leakage in the system of available.

**Step -5:** Start compressor and timer while raising the
compressor pressure to its design pressure (**P _{2}**). Note time taken (

**T**) in minutes for air compressor to reach pressure P

_{2}from initial pressure P

_{1}

**Step -6:** After Getting P_{1}, P_{2}, V,
T Use below Formulae

**Q = (P _{1}-P_{2})/P_{0} X (V / T)**

Where

Q = Flow in Nm3/Min

P_{1} = Initial Pressure in Kg/cm2 (a)

P_{2} = Final Pressure in Kg/cm2 (a)

P_{0} = Atmospheric Pressure in Kg/cm2 (a)

V = Volume of receiver and pipeline

T = Time taken to build-up pressure P_{2} from P_{1}.

The above equation is relevant where the compressed air temperature is same as the ambient air temperature, i.e., isothermal compression. In case the actual compressed air temperature at discharge, say t2 deg C is higher than ambient air temperature say t1 Deg C (as is usual case), the

FAD is to be corrected by a factor (273 + t1) / (273 + t2)

Example :

Air Compressor FAD trail was taken of a compressor for 550 Nm3/Hr Capacity compressor and

Receiver Volume 6 m3, Line holdup = .25 m3

Initial pressure
P_{1} = 1.5 Kg/cm2(a), Final pressure P_{2}= 8 Kg/cm2(a),

Amb Pressure
P_{0}=1.026Kg/cm2(a)

Time Taken For pressure rise T=5.2 min

Air Inlet Temp = 25 Deg C, Air Outlet Temp 40 Deg C

Lets us find FAD of compressor

Free Air Discharge = (8-1.5)/1.026 X (6.35/5.2) = 8.2 Nm3/min

= 492Nm3/hr

FAD after Temp Correction = 492X (273 +25)/(273+40)

= 468.4 Nm3/hr

Capacity Reduction of compressor = (550-468.4)/650 = **14.8%** ( Need to be investigated)

**Specific power consumption Calculation** :

After finding FAD of air compressor, we are having output available with us now, input power data can be collected from power meter. Output by input power shall be specifc power consumption of compressed air.

**Useful ****reference :**

For Air compressor capacity, Specific power consumption calculation and recommendation excel sheet, please click below (for reference only)

You May be interested in below articles, Please check :